User name Nanda
Log entry time 20:50:23 on October27,2000
Entry number 51112
keyword=Chamber Gas Empty Alarm
Chamber gas supply alarm at 17:45.
Ethane pressure low.
Upon inspection at the gas shed, noticed that the first bottle was
empty, the 2nd bottle was full but had its valve closed. Opened valve.
Manually switch to 2nd bottle in the controller. Hit reset.
Gas flow back to normal now. Replaced the empty ethane bottle.