User name eschulte
Log entry time 17:20:41 on July29,2006
Entry number 176030
keyword=Adjusted JT Valves Loops 2&3
Adjusted JT valves on loops 2&3 to keep loop 3 at about 30W with beam on 10uA (was about 20). At 20W we were getting very low HPH power outputs with some beam current fluctuations. Total 15K flow <23 g/s Halls A & C.