User name ckeith
Log entry time 19:13:15 on January15,2002
Entry number 80339
keyword=cryotarget control status
Condition of cryotarget controls as of 1-15-01 at 19:00:
To the best of my knowledge everything is working ok except:
1) Fan controls -- low priority since fan settings are rarely adjusted;
2) Target lifter -- GUI controls are functional; lifter occassionally stops before move is complete. An IOC reboot should fix this. Debug ongoing.
3) Heater PID -- the CRON job that normally maintains the most up-to-date
version of the PID settings has been modified to run on the new HallA server. It
will be started tomorrow.
4) Alarm limits -- these are no longer automatically written to the IOC bootscript.
Acceptable values are "hard-coded" for now. I am working with ACE to initiate
a remote synch between the control computer and server to allow auto update for the