User name Reitz
Log entry time 06:26:20 on January29,2002
Entry number 81186
keyword=FPP gas supply
During the night, we got several gas alarms. And the gas flow through the
VDCs seems to be low. Jack told us, that this is because of too much
gas flow through the FPP.
For the moment, we turned down HV of FPP and stopped the gas flow to
FPP in the gas shed.
**** dont turn on FPP HV **** at the moment
During next access we will adjust FPP gas flow in the detector hut !!!
Gas flow for FPP (in gas shed) will be turned on 30 minutes before the