User name H. Benaoum/jpchen
Log entry time 13:36:58 on July24,2005
Entry number 149292
Turned out the vent valve was not closed. So we closed the vent valve.
Switched to a new bottle of helium before started cool-down.
Target cooled-down completed.
Normal condtions for target now : CHL flow around 20 (HP heater power=180w) and 200psi for pressure.
The beam compensation turned back on. Fan turned back to 60 Hz.